Sewer lateral inspection starting from offset at sidewalk to the right of driveway as you look at the house. ABS pipe from that point, all the way to the back of the house were there is a clean out located by the water heater. There was one section under the house that appeared to have some root intrusion, but looks good for the time being. There were some dips in the line, but it did not seem to be causing any problems. I would recommend fixing the offset near the sidewalk and putting a clean out near the front of the house.